- Steam Theory
- 1. Basics of Steam
- 2. Steam Heating
- 3. Basics of Steam Traps
- 4. Steam Trap Selection
- Steam Trap Selection: How Application Affects Selection
- Steam Trap Selection: Understanding Specifications
- Steam Trap Selection: Safety Factor and Life Cycle Cost
- Traps and Orifices Part 1
- Traps and Orifices Part 2
- Casting vs. Forging
- Don't Get Steamed : Selecting Steam Trap Design
- Understanding Steam Traps
- 5. Steam Trap Problems
- 6. Steam Trap Management
- 7. Water Hammer
- 8. Steam Quality
- 9. Steam Distribution
- 10. Condensate Recovery
- Introduction to Condensate Recovery
- Returning Condensate and When to Use Condensate Pumps
- Condensate Recovery: Vented vs. Pressurized Systems
- Condensate Recovery Piping
- What is Stall?
- Methods of Preventing Stall
- Cavitation in Condensate Pumps
- Steam Heat Exchangers are Underworked and Over-Surfaced
- Stop Knocking Your Condensate Return
- 11. Energy Efficiency
- 12. Compressed Air / Gas
- 13. Other Valves
Principal Applications for Steam
Steam is used in a wide range of industries. Common applications for steam are, for example, steam heated processes in plants and factories and steam driven turbines in electric power plants, but the uses of steam in industry extend far beyond this.
Here are some typical applications for steam in industry:
In the sections that follow, we will discuss various types of applications for steam, and provide some examples of steam-using equipment to illustrate them.
Steam for Heating
Positive Pressure Steam
Steam is typically generated and distributed at a positive pressure. In most cases, this means that it is supplied to equipment at pressures above 0 MPaG (0 psig) and temperatures higher than 100°C (212°F).
Heating applications for positive pressure steam can be found in food processing factories, refineries, and chemical plants to name a few. Saturated steam is used as the heating source for process fluid heat exchangers, reboilers, reactors, combustion air preheaters, and other types of heat transfer equipment.
Shell and Tube Heat Exchanger
In a heat exchanger, steam raises the temperature of the product by heat transfer, after which it turns into condensate and is discharged through a steam trap.
Superheated steam heated to 200 – 800°C (392 - 1472°F) at atmospheric pressure is particularly easy to handle, and is used in the household steam ovens seen on the market today.
The use of steam for heating at temperatures below 100°C (212°F), traditionally the temperature range in which hot water is used, has grown rapidly in recent years.
When vacuum saturated steam is used in the same manner as positive pressure saturated steam, the temperature of the steam can be quickly changed by adjusting the pressure, making it possible to achieve precise temperature control unlike applications using hot water. However, a vacuum pump must be used in conjunction with the equipment, because merely reducing the pressure will not drop it to below atmospheric pressure.
Heating with Latent (Steam) Heat
Compared with a hot water heating system, this system offers fast, even heating. The set temperature is rapidly reached without causing unevenness in temperature.
Steam for Propulsion/Drive
Steam is regularly used for propulsion (as a driving force) in applications such as steam turbines. The steam turbine is a piece of equipment that is essential for the generation of electricity in thermal electric power plants. In an effort to improve efficiency, progress is being made toward the use of steam at ever-higher pressures and temperatures. There are some thermal electric power plants that use 25 MPa abs (3625 psia), 610°C (1130°F) superheated, supercritical pressure steam in their turbines.
Superheated steam is often used in steam turbines to prevent damage to equipment caused by the inflow of condensate. In certain types of nuclear power plants, however, the use of high temperature steam must be avoided, as it would cause problems with the material used in the turbine equipment. Instead, high pressure saturated steam is typically used. Where saturated steam must be used, separators are often installed in the supply piping to remove entrained condensate from the steam flow.
Besides power generation, other typical propulsion/drive applications are usually for either turbine-driven compressors or pumps, ex. gas compressors, cooling tower pumps, etc.
The driving force from the steam causes the fins to turn, which then causes the rotor on the attached power generator to rotate, and this rotation generates electricity.
Steam as Motive Fluid
Steam can also be used as a direct “motive” force to move liquid and gas streams in piping. Steam jet ejectors are used to pull vacuum on process equipment such as distillation towers to separate and purify process vapor streams. They are also used for continuous removal of air from surface condensers, in order to maintain desired vacuum pressure on condensing (vacuum) turbines.
Ejector for Surface Condenser
High pressure motive steam enters the jet ejector through the inlet nozzle and is then diffused. This creates a low pressure zone which entrains air from the surface condenser.
In a similar type of application, steam is also the primary motive fluid for secondary pressure drainers, which are used for pumping condensate from vented receiver tanks, flash vessels, or steam equipment that experiences stall conditions.
Steam for Atomization
Steam atomization is a process where steam is used to mechanically separate a fluid. In some burners, for example, steam is injected into the fuel in order to maximize combustion efficiency and minimize the production of hydrocarbons (soot). Steam boilers and generators that use fuel oil will use this method to break up the viscous oil into smaller droplets to allow for more efficient combustion. Flares also commonly use steam atomization to reduce pollutants in the exhaust.
Steam Assisted Flare
In flares, steam is often mixed in with the waste gas before combustion.
Steam for Cleaning
Steam is used to clean a wide range of surfaces. One such example from industry is the use of steam in soot blowers. Boilers that use oil or coal as the fuel source must be equipped with soot blowers for cyclic cleaning of the furnace walls and removing combusted deposits from convection surfaces to maintain boiler capacity, efficiency, and reliability.
Boiler Tube Cleaning with Soot Blower
Steam released out of the soot blower nozzle dislodges the dry or sintered ash and slag, which then fall into hoppers or are carried out with the combusted gasses.
Steam for Moisturization
Steam is sometimes used to add moisture to a process while at the same time supplying heat. For example, steam is used for moisturization in the production of paper, so that paper moving over rolls at high speed does not suffer microscopic breaks or tears. Another example is pellet mills. Often mills that produce animal feed in pellet form use direct-injected steam to both heat and provide additional water content to the feed material in the conditioner section of the mill.
Pellet Mill Conditioner
The moisturizing of the feed softens the feed and partially gelatinizes the starch content of the ingredients, resulting in firmer pellets.
Steam for Humidification
Many large commercial and industrial facilities, especially in colder climates, use low pressure saturated steam as the predominant heat source for indoor seasonal heating. HVAC coils, often combined with steam humidifiers, are the equipment used for conditioning the air for indoor comfort, preservation of books and records, and infection control. When the cold air is heated by the steam coils, the relative humidity of the air drops, and it must then be adjusted to normal levels with addition of a controlled injection of dry saturated steam into the downstream air flow.
Steam Humidifier in Air Duct
Steam is used to humidify air within an air duct before the air is distributed to other regions of a building.
|What is Steam?||Types of Steam|