- Steam Theory
- 1. Basics of Steam
- 2. Steam Heating
- 3. Basics of Steam Traps
- 4. Steam Trap Selection
- Steam Trap Selection: How Application Affects Selection
- Steam Trap Selection: Understanding Specifications
- Steam Trap Selection: Safety Factor and Life Cycle Cost
- Traps and Orifices Part 1
- Traps and Orifices Part 2
- Casting vs. Forging
- Applications of Different Types of Steam Traps
- Don't Get Steamed : Selecting Steam Trap Design
- Understanding Steam Traps
- 5. Steam Trap Problems
- 6. Steam Trap Management
- 7. Water Hammer / Risk Mitigation
- Water Hammer: What is it?
- Water Hammer: The Mechanism
- Water Hammer: Cause and Location
- Water Hammer: In Steam Distribution Lines
- Water Hammer: In Equipment
- Water Hammer: In Condensate Transport Piping
- Water Hammer: Conclusion
- Mitigation of Water Hammer in Vertical Flashing Condensate Transport Piping
- Stop Knocking Your Condensate Return
- Steam Trap Management: Do Something; Anything. Please!
- Steam System Optimization and Risk Mitigation
- Risk Based Methodology for Industrial Steam Systems
- 8. Steam Quality
- 9. Steam Distribution
- 10. Condensate Recovery
- 11. Energy Efficiency
- Tips to improve steam plant efficiency
- Advice on Winter Preparation for Steam Systems
- Insulating Traps
- Steam Compressors
- Why Save Energy?
- Management Strategies for Conserving Energy
- Recovering Steam Clouds and Waste Heat
- Handle Steam More Intelligently
- Optimize the Entire Steam System
- Use Available Data to Lower System Cost
- 12. Compressed Air / Gas
- 13. Other Valves
Heating with Steam
Steam is one of the most common and effective heat transfer mediums used in industry, but it is not the only medium available. Other fluids such as hot water and oil are also used for indirect heating in heat exchangers. The following series of articles will focus on the advantages of using steam compared to hot water or oil for heating.
Advantages of Steam Heating
Heating with Hot Water or Oil
Heat transfer from a liquid medium such as hot water or oil utilizes the medium’s sensible heat. The liquid is supplied at elevated temperatures to the heat exchanger. As the liquid gives off thermal energy, its temperature decreases, exiting the exchanger at a lower temperature. The amount of energy released per unit of heat transfer medium is relatively low (typically around 17 kcal/kg, or 30 Btu/lb).
Heating with Steam
Steam is supplied in a gaseous state to the heat exchanger. Heat transfer with saturated steam utilizes the latent heat of steam, releasing a large amount of energy as it condenses (changes to the liquid state). Liquid condensate exits the heat exchanger at close to saturated steam temperatures. The amount of energy released per unit of steam is high (up to 539 kcal/kg, or 970 Btu/lb, and higher with vacuum steam).
Summary of Benefits
Utilizing latent heat (steam heating) for heat transfer is far more effective than utilizing sensible heat (hot water or oil heating), as a much higher amount of energy is released in a shorter period of time. This offers the following benefits:
To understand the reasons behind these properties and advantages, read the next article on the Steam Heating Mechanism.
|How to Read a Steam Table||Steam Heating Mechanism|